Wood pellet 6 - 8 mm
Boilers class 5Automatic fuel ignition, extinguishing the furnace and fire support system after reaching the desirable temperature, provides the possibility of continuous operation of the boiler and cooperation with the C.W.U. accumulator in the summer time
Wood pellet 6 – 8 mm
Semi-automatic boilers„Semi-automatic” boilers allow the combustion of any kind of solid fuels, such as: hard coal, seasoned wood, fine coal with the solid-flammability of up to 20 hours. Boilers are equipped with electronic air blowing control.
Manual boilers„Manual” boilers are very popular due to their versatility. They are designed for combustion of hard coal and firewood. All versions are designed for the installation of the draught regulators.
Seasoned woodHard coal
Kitchen with stoveKitchen with stove ZOSIA is the modern, aesthetic and highly efficient device designed for heating single-family houses, garages and utility rooms..
EquipmentIn this section you can find the exact parameters and description, which constitute standard equipment of our products. This will allow you for the detailed analysis and comparison of such important elements of the boiler, as: feeder, controller, fan, etc.
AccessoriesThis section presents the accessories, in which our products can be equipped. All accessories are optional and are at extra charge. You can purchase them from our distributors.
Dodano: 09:01, 17/01/2017
During the break in the operation of the airflow of the boiler the temperature of the furnace drops below the temperature of ignition of gases generated by fuel, which increases their concentration in the combustion chamber. Re-switching the fan results in the increase in the temperature of ignition of gases in a short time (above 300-400 degrees of Celsius), which causes their sudden ignition. Combustion of accumulated gases increases the pressure, which results in the explosion.
Additional causes of the accumulation of gases in the combustion chamber of the boiler:
– incorrect chimney draught
– poor fuel quality
– too rare frequency of blow cycles
– no heat reception
– heat consumer twisted or throttled with thermostatic valves
– aerated system or boiler
– boiler incorrectly matched to the usable area
– improperly set parameters of boiler control